Plans Review Information & Permitting Information
If you have any questions please contact our office during our normal business hours of 7 a.m. - 3:30 p.m. Monday - Friday at 256-233-8723.
On January 11, 2021, the Athens City Council passed and adopted the International Code Council 2018 set of codes for all city departments. There will be a 6 month period in which plans will still be accepted under the 2009 code set. As of July 1, 2021, ALL plans submitted MUST be submitted under to 2018 code set.
This adoption also brought forth a new fee schedule for inspections and permits. The fee schedule will be posted on this page for reference. Please contact this office with any questions.
- The City of Athens operates under the 2009 International Fire Code. As of July 1, 2021 the City of Athens will operate under the 2018 International Fire Code.
- The Fire Prevention office requires site plan, building, fire alarm, fire sprinkler and other applicable drawings to be submitted for review before any project begins. Send two (2) sets of stamped and signed drawings to the physical address listed on the right side of this page. If you submit drawings for review, you MUST be licensed by the State of Alabama for the type of plans your are submitting when you submit. At this time there is no fee for review of plans, however this is subject to change at any time.
- We require any new construction, renovation, or change of occupancy to have a Knox Box® installed for emergency entry by the fire department.
- We require any building requiring a fire sprinkler system to have a stand-alone FDC away from the building with Knox Box® locking caps installed.
- Any commercial kitchen hood and suppression installation must be inspected and tested prior to use. A smoke test is required for testing the hoods. Please contact the fire prevention office to schedule these inspections/test.
- We conduct inspections throughout the construction process and a final inspection is required before a Certificate of Occupancy (C-O) will be issued. All fire related systems must pass at the final inspection or the C-O will not be issued until they do.
- We conduct fire alarm and fire sprinkler acceptance tests upon completion of a system. These are complete tests, and the systems must function properly or the test will be considered failed. For fire alarm systems, smoke (no magnets) is required to test detectors during an alarm test.
- All permitting is done through the Athens Building Department(we are located in the same building) phone# 256-233-8715. At this time there is no permit fees for fire alarms or fire sprinklers. This will change on July 1, 2021. As of July 1, 2021, a new few structure will go into effect.